Plumbing & HVAC Repair Company near Wylie TX
Chrome Heating & Air provides 5 star rated air conditioning repair, heating and plumbing services to the residents of Wylie, TX and the surrounding areas. When your plumbing or air conditioning system isn't working as efficiently as you would like contact Chrome for 5 Star Service and we'll help you save money on your HVAC system.
Heating, AC & Plumber Service FAQs
Home air conditioners should be serviced at least once a year in Wylie, TX. Getting your home air conditioner on a maintenance plan has many benefits:
- It extends your air conditioner’s lifespan
- It increases the efficiency of your air conditioner
- It allows you to spot any issues before they become worse
The average cost to repair a home air conditioning unit in Wylie, TX is around $250-$400. However, some repairs are more extensive, which can cause the price to fluctuate. For example, it can cost up to $1,500 to repair a refrigerant leak due to the cost of the repair and the amount of refrigerant it takes to recharge your unit. To learn more about getting your home air conditioning unit repaired, call us today.
Yes, plumbers install hot water heaters in Wylie, TX. A plumber’s knowledge of building codes, plumbing, wiring and gas lines makes them the most qualified person to install your hot water heater. If you are thinking about having a hot water heater installed in your home, contact Chrome Heating, Air & Plumbing today.
Read our reviews below to find out why your neighbors consider us to be their go-to AC repair expert and plumber near Wylie, TX.
for Wylie, TX
Our Reviews by City
He was good
Willie - Wylie, TX 75098
Excellent emergency service.
Betty - Wylie, TX 75098
Courteous and professional
Anderson - Wylie, TX 75098
Nick was very friendly, informative, courteous and professional throughout the troubleshooting and checkout and maintenance of our system. It was a pleasure to deal with him!
Aubrey - Wylie, TX 75098
Mr - Wylie, TX 75098
They did a great job everything works good thanks
Spring HVAC Repair Service for a residential homeowner in Wylie with an A/C system not working. Upon arrival re inspected units. Outdoor coils had slight dust on them, took panels off and sprayed off with water hose to clean. Found that the return by downstairs thermostat was humming/rattling a little, screwed return door shut so noise would stop, filter gets replaced At the unit. For the insulation on the suction line outside was only missing about two inches of insulation. Both systems are working properly. Customer happy on departure.
Air Conditioning system maintenance for a residential customer. Came out on 1 system maintenance Checked bearings checked blades checked UV bulb checked ductwork checked contactors checked surge protectors checked Amp draws checked electrical connections checked filter checked drain line checked coils checked run capacitors Found: The UV bulb is out. 80mfd run cap is bad
Came out on service call 25seer hp lennox Code at tstat 426 ou excessive allert lockout Codes on outside unit are e431, e433, e441 High amprage on compressor Case # 2080506 Greg tech support tech. Testing in cooling Amp draws for compressor go up to 16 and shut off Testing In heat mode Amp draws for compressor go up to 16 and shut off Omhm out compressor plug all are .08 Tested legs to ground over continuity and compressor is not grounded Incoming volts to unit 241 Recommendations to replace compressor and inverter under warranty. Vacuum and 15lbs of refrigerant. In order for the unit to properly run in a.c. or heat. (At this time only aux heat is properly functioning.) Good Amp draws on heat strips and blower motor as well as condenser fan motor. Customer does not approve repair at this time.
Came out on 2 system maintenance Checked bearings checked blades checked run capacitors checked contactors checked pressures checked electrical connections checked duct work check insulation checked filters checked Amp draws checked coils checked temp split checked drain lines Units are working at this time.
No heat service call in Wylie. Inspection of Trane unit found no gas pressure from the gas valve. The unit gas valve was turned off and turned it on and restarted the unit. Trane unit is running properly.
Came out on 1 system maintenance Checked bearings checked contactor checked blades checked housing checked temp split checked pressures checked drain line checked both coils checked smo fried checked electrical electrical connections Found Neither Indoor and outdoor units have surge protection Condenser contactor is showing signs of age a little black and pitted on load side of 1.5 Pole Condenser has no hard start kit It allows compressor to not take so much of an amount during during start up extending the life of the compressor
Came out on 1 system service call Checked bearings checked Amp draws checked drain line checked filter checked electrical connects checked temp split checked pressures checked contactors checked capacitors checked blades inspected insulation levels inspected duct work Found No surge protection on unit. No IAQ (UV LIGHT KIT.) High Amp draw on condenser motor meaning possible part failure.
Upon arrival found system in off mode. Homeowner said there was smoke coming out of vents and error codes on tstat. Checked inside unit and found filter clogged. Filter is a Lennox healthy home filter x6675. Checked heat strips with continuity and they were good. Pulled blower and inspected heat strips. Found layers of dust and build up on the 2nd and third set of strips. Recommended replacing heat strips or cleaning. Was getting a communication error for outdoor unit. Found splice in wall at condenser system would need a new Tstat wire to outdoor unit. Checked pressures and amp draws on compressor. Both were good compressor pulling 10.4 out of 24.7. System is on and running, recommended adding a air scrubber uv light so build up doesnâ€™t happen again on heat strips. Emailed repairs over homeowner wants to think about it.
Performed a one system maintenance checking heating. Checked all electrical, mechanical and safety components. Checked amp draws, cleaned flame sensor, checked systems sequence of operation, checked capacitor, and changed out customer supplied filter. System is heating properly at this time.
Upon arrival found system working. Checked thermostat alert history and found two error codes. One for a high pressure switch and lost of communication. Turned system on a/c and checked pressures. Pressures were good. Coil was clean. Fan motor was working properly. Switched system to heat pump mode and pressures were good. Let system run for 15min in heat mode to see if pressures would rise and they stayed steady. No faults found for high pressure. On communication error found where the wire had been spliced and found water damage around wire nuts. Recommended repairing wire. Homeowner approved repair and repair wire. Turned system back on and system is now working properly.
Everything was good let them know to put frost proof hose nine cover on.
Checked amp drawâ€˜s on electric heat strips on blower motor check pressures on heat pump, checked amp drawâ€˜s on condenser fan motor and compressor, checked filter
Checked amp draws on inducer fan motor and blower motor, cleaned flame sensor checked air filter, checked safety devices, checked heat exchanger it was good, check igniter
Performed a one system maintenance checking heating. Checked all electrical, mechanical and safety components. Checked gas pressure, heat exchanger, amp draws, capacitor, cleaned flame sensor. Furnace is heating properly at this time. Recommended replacing the filter.
Performed a two system maintenance checking heating. Checked inside air handlers electrical and mechanical components, checked amp draws, heat strips. Checked pressures amp draws and capacitors. Found that both condenser coils need to be washed. Downstairs contactor is pitted and shows some wear. And recommended start assists for both units. Homeowner waived repairs.
Dug out approximately 3 foot of water and got rope through concrete and pumped out water that was in the ditch
Did spring maintenance, customer said vents made humming noise in the front rooms, checked to make sure everything was clean, and it was, so tightened the registers to help. Found mold on drain lines, cleaned them off and recommended a UV light and monthly vinegar and bleach in drain lines. Unit was also short 1Ib of refrigerant, charged by subcooling.
Completed installation of whole home air purification system through UV light purification. This will keep Miss. Lilyâ€™s home free of airborne bacteria, viruses, and allergens.
Found hot and cold water lines in wall in upstairs bath ffrozen and burst. Replaird both hot and cold water lines
I found unit operating in heat pump mode, weather is too cold for heat pump so I turned on heat strips... emergency heat. Unit is working properly
Completed one system matience on downstairs system ( heat pump) filter needs to be changed 16x25x4, I checked refrigerant pressures, ampersges, safetyand operationof heat pump. Cuatomer hasn't been satisfied with our service starting at instalation of units. Customer stated that there were problems after installation and problems ever since with the units. She is considerably going with another matience company.
Reviewed options given previously. Also added a 2 stage system option with insensitive like topping off insulation and UV light.
Completed one system fall matience. Unit was cleaned and tested for operation and safety. Unit passed inspection with no concerns for safety for failure. Pictures attached