Chrome Heating & Air provides top notch air conditioning, heating and plumbing services to the residents of The Colony, TX and the surrounding areas.
Some things that are included in the AC maintenance plan through Chrome Heating Air & Plumbing in The Colony, TX include:
There are even more benefits to getting an AC maintenance plan, such as lower costs on your energy bills. When your AC unit is well maintained, it runs more efficiently and lasts longer. Call us today to learn more about our AC maintenance plan.
It costs around $300-$1,500 to fix and repair a broken home AC system in The Colony, TX. Although, the price can vary due to:
If your AC system is broken, the cost to repair it might end up costing you more than if you were to replace your unit. To find out more about repairing your home AC system, call Chrome Heating, Air & Plumbing.
The average cost to replace your home air conditioner in The Colony, TX is around $3,500-$6,000. Some factors that will impact the overall cost include:
- The size of your home
- The type of air conditioning unit you want installed
- If you also plan to get new duct work installed
Plumbers have various technologies in addition to their plumbing knowledge that help them to find leaks, ranging from ground microphones, heat scanners and video inspection tools. Plumbers are able to detect the general area of a leak without the aid of technology. Although, with additional tools, a plumber is able to detect a hidden leak behind a wall without having to use intrusive methods. If you believe you have a water or gas leak, contact us today and we can help!
Read our reviews to find out why your neighbors consider us to be their go-to HVAC expert and plumber in The Colony, TX.
for The Colony, TX
Our Reviews by City
Fall Tune Up
Bernard - The Colony, TX
I was not home. My wife said John was courteous. Explained what he did and spent time reviewing his findings and recommendations. Overall a very positive experience.
Chalres - The Colony, TX
Quick Service but Bad news
Curt - The Colony, TX
The service was quick but the tech found a problem in that the unit may need to be replaced. That is not a happy thought even though he go the unit cooling better.
Great price, great install
Dorothy - The Colony, TX
They beat the other quotes I had for same hardware
Friendly Technician, Great Service
Mr Joe C - The Colony, TX
Joan - The Colony, TX
Fast, nice and honest!
Felix - The Colony, TX
I found Rheem water heater(tankless) has frozen, burst and leaked. We are looking into options on what next step is.
Completed one system fall matience on 2019 lennox furnace. Furnace was still like new and running properly at this time. FILTER IS APRIL AIR 210 and will be ready to be changed come spring time. Estimates for insulation and membership renewal attached.
Performed tune up of heating system, unit is working properly at this time
Completed one system tub unit heat checkup. Door above tub needs to be replaced. Unit is operating correctly at this time. Need to get pricing on tub door. Size 31x45 inches pictures attached. Also Completed a plumbing inspection. Going to leave estimate for labor to replace kitchen fixtures. Pictures and estimates attached
Checked wiring connection at stat, hub and furnace. Cycled power and tested. Unit is working properly. Customer would like to consider chrome via membership.
Pulled out old coil, installed new, pressure tested, pulled vacuum, and charged to factory specs. Unit is cooling properly at this time.
Completed two system matience on 2 year old lennox systems. I checked operation, voltages, blower motor amperages, filters and safety switches to the furnace. At this time both units are working properly.
Conpleted 2 system fall matience recommended code upgrades and capacitor. Customer also was saying the downstairs condenser was still making a loud noise on startup after nathan and I put a hardstart kit on about a month ago. I tested LRA and startup noise three times and unit was 64/81 max amps and didn't seem overly noisy to me.
Completed one system estimate/diagnostic. See all options for details. Customer still getting bids. Another company pulled up as I was leaving.
Emailed customer bids for replacement. Customer is receiving one more bid. Already received bid from Costco at 18.3k for same work. Customer wants to calculate some costs and will reach back tomorrow or Saturday. See options for details.
Completed a one system diagnostic. Damper 12â€ was not closing and dropping communication. Reset system and purged damper. System is operating properly at this time. Customer signed up for annual club agreement for two systems.
Added leak search to system. System was heavily under charged. Will need to return tomorrow to inspect complete system for leak. Returned 8/25/2020 and found leaks in 4 year old Lennox Evaporator coil for upstairs system (see stretched photos.) gave customer options on warranty part only vs replacing coil out of warranty and getting a new part and labor warranty.
One system diagnostic. Added start assist kit to upstairs Lennox system. System amperage dropped by 42% and is a lot quieter. Customer also signed up on monthly club agreement.
Gave customer estimate. Customer wants discounts but not willing to move forward with work. Emailed customer options. Customer will be getting bids from Costco and Home Depot.
AC repair and tune-up.
Customer has a leak in ac system coil. Inspected the complete system and gave customer a quote on a new 4 ton Lennox two speed and single speed, 16 seer system after completing a manual J heat load calculation that measures the exact size system needed for the home based on windows, doors, insulation, and even the direction the home faces.
Installation of a new evaporator coil and new Lennox condenser
Inspected the complete system and gave customer a quote on a new 5 ton Lennox two speed,16 seer system after completing a manual J heat load calculation that measures the exact size system needed for the home based on windows, doors, insulation, and even the direction the home faces.
Fall maintenance on a 21 year old Hvac System.
Duct leaking. Diagnostic: Needs to seal up plenum with tape and spray glue.