HVAC Contractor & Plumbing Company near Greenville
Chrome Heating & Air is proud to provide Greenville, TX with the kind of heating, cooling and plumbing service we would like for our own families.
AC, Heating & Plumbing Service FAQs
The types of home air conditioner repairs that are common in Greenville, TX include:
These repairs are usually a result of the hot and humid summers Texas residents are no stranger to. One way to prepare for these common repairs is to have your air conditioner regularly serviced. Contact us today to learn more about air conditioning maintenance.
It costs around $250-$1,600 to fix an air conditioner leak in Greenville, TX. The following are possible reasons that your air conditioner is leaking, ranked from least expensive (top) to most expensive to repair (bottom):
It is natural for your unit to have condensation as a result of the inner workings of the unit itself. Although, when there is an increase in condensation that results in a leak, that is an indication that there is an issue with your air conditioner. Call us today to get your air conditioner leak repaired.
Yes, plumbers fix water leaks in Greenville, TX. Regardless of the type of water leak, a plumber can locate a leak and diagnose how to repair it. Even if you cannot see the leak, a plumber has tools that allow them to find leaks even when they are behind walls. Plumbers are also able to assist you with standard water leaks from a fixture such as a sink or a toilet. If you have a water leak that needs to be repaired , contact Chrome Heating, Air & Plumbing today .
See how we always meet the home services needs of our Greenville, TX customers and why they consider us their plumber and HVAC company in the reviews below!
for Greenville, TX
Our Reviews by City
Great service as always.
Rutter - Greenville, TX 75402
Rutter - Greenville, TX 75402
Jorge is great he always makes sure you are happy with his service. I have always been happy with Jorge. 👍🏼
Gary - Greenville, TX 75402
George is great. He always gives me great customer service.
Tech delivered great service.
Mr Rutter - Greenville, TX 75402
Came out on one system maintenance. Checked Amp draws checked temperature split over unit checked electrical connections checked contactor checked run capacitors checked bearings checked blades checked drain lines checked coils checked air scrubber uv light Found Dual run cap suppose to be 40/10 we are reading 39.5/7.4 which is bad needs to be replaced No surge protection on any equipment. Dusty duct work causing motor to work harder.
Checked amp drawâ€˜s on blower motor electric heat strips, checked amp drawâ€˜s on condenser fan motor Compressor, checked pressures and tested defrost cycle
Completed one system fall matience on 3 year old lennox air handler. Unit needs a new filter 16x25x4, but other than that system is operating correctly. Unit also already has UV light air purification.
Ran a new low voltage wire from the air handler to the condenser.
Completed installation of a Lennox 16 seer heat pump start up.