Local Plumbers, Heating & AC Repair near Dallas
Chrome Heating, Air & Plumbing is proud to provide Dallas, TX with the kind of heating, cooling system and plumber repair services we would like for our own families. Is it time to replace that old HVAC system? Are your HVAC systems providing the energy efficiency you are looking for? Need emergency air conditioning repair service? We also repair and install tankless water heaters!
Our air conditioning company HVAC technicians and plumbers are background checked and Google Guaranteed.
HVAC & Plumbing Service FAQs
The price to have a plumber clear a drain in Dallas, TX is typically between $200-$300. Some things that can impact the overall price include the complexity of the issue and the contractor’s hourly rate. Having a plumber clear your drain guarantees that your drain gets cleared correctly and quickly. Additionally, if there are any deeper issues, a plumber will be able to spot those and diagnose them for you. If you need your drain cleared , give us a call today .
Your home air conditioner might have a leak due to:
Some air conditioner leaks can be as simple to fix as replacing dirty air filters, whereas other leaks can be more complex, such as repairing a refrigerant leak. If you are experiencing a leak from your home air conditioner, contact Chrome Heating, Air & Plumbing.
Yes, an air conditioner compressor can be repaired. However, depending on the issue, it may be cheaper to replace your air conditioner compressor rather than repairing it. If your compressor is older or it has required many repairs in the past, it is usually more cost effective to have it replaced with a newer and more efficient compressor. Contact us today to have your air conditioner compressor repaired or replaced .
It costs around $250-$400 to fix and repair a central air conditioning system in Dallas, TX. Although, the price can vary depending on how severe the problem is and if any replacement parts are required. For example, if your evaporator coil is faulty, it can cost up to $1,200 to replace it. Call us today to get your central air conditioning system repaired !
See how we always meet the home services needs of our Dallas, TX customers and why they consider us their plumber and HVAC company in the reviews below!
for Dallas, TX
Our Reviews by City
Ashley - Dallas, TX
Ranee - Dallas, TX
Parkway - Dallas, TX
Jeremy is definitely a seasoned tech. Diagnosed the problem quickly and had the parts on hand in two days.
Vickey - Dallas, TX
Professional and On time
Jackie - Dallas, TX
Poor customer service
Brent - Dallas, TX
I was cancelled on multiple times last minute, misled on pricing, and then overcharged for my service with the owner of the company lying directly to me. The actual plumber that performed the work was nice and did a good job.
Lasco - Dallas, TX
Jacqueline - Dallas, TX
As always whenever I need service for my unit the techs at Chrome respond in a timely manner. They know their stuff and are very thorough in their assessment of the problem and how best to correct it. They listen to my concerns and explain what I need in terms I can understand. And they stand behind their work.
Awesome work ethic
Lasco - Dallas, TX
B - Dallas, TX
Sharon - Dallas, TX
Vickey - Dallas, TX
Professional, through, friendly, knowledgeable, communicated with me throughout the process of inspecting and installing
George - Dallas, TX
Very timely, thorough with explanations and covers options where applicable.
Finch - Dallas, TX
Good service and good value.
Gigoux - Dallas, TX
Great service. Had my unit up and running in minutes
xxxPhelps - Dallas, TX
Very happy to see Jorge after two days of no air
I'm reviewing Jorge
xxxAnderson - Dallas, TX
This survey is for our 2nd appointment with Jorge.
Great service price too high
xxxAdams - Dallas, TX
Michael - Dallas, TX
They quickly diagnosed the problem and ordered the needed part immediately.
Best Service to date
Mrs price - Dallas, TX
Jorge was polite and professional and they gave me prompt service with a smile.
Honest fair service with quality work
James - Dallas, TX
Always honest fair service
Vivian - Dallas, TX
Although the serviceman was young, he was very impressive with knowledge of his field and with his people skills I felt respected as a person and valued as a customer
Mia - Dallas, TX
Tim - Dallas, TX
Courteous and knowledgable men. Michaela the receptionist worked us in and was much appreciated.
Andrea - Dallas, TX
Great service, very professional and knowledgeable
Dallas resident wanting an estimate and Upon arrival found system cooling. Homeowner stated that the thermostat would lose power, turned system on and checked indoor unit, found water in emergency pan but trap was empty. After letting system run found that the main drain line was stopped up causing float switch to turn off thermostat. Checked outdoor units pressures, amp draws and capacitor all looked good. System appears to be tied into tub drain somewhere. Homeowner said that the tub has been draining slow. Homeowner wanted to get a plumber out to look at tub drain first.
Commercial service call in Dallas Upon arrival found food room not cooling. Checked condenser on roof top and found contactor pulled in but unit not running. Found that the system had a bad 70/5 dual run cap. Replaced cap and system came on. Checked amp draws and pressures, checked supply air 57 and return air at 77. System is now cooling properly at this time.
Springtime Air Conditioning Repair for a residential customer near Wolf Creek. Upon arrival found the system not cooling as well as it should. Checked inside unit and found everything operational, checked inside evaporator coil and found two big oil spots on bottom front left and right corners. Homeowner stated that they put refrigerant in it two weeks ago and reading pressures now system is a little low. Checked what kind of warranty system has and system is still under parts and labor warranty but only has 3 months left. Parts and labor are covered if repair is done by a York dealer. Only parts are covered if work is performed by a non-authorized dealer. Gave estimate for warranty repairs since were a Lennox dealer. Recommended homeowner getting a York dealer out to replace the evaporator coil.
Springtime Residential HVAC Maintenance near Buckner Terrace. Came out today on maintenance. Checked temp split checked pressures checked filter aprilair 210 checked coils checked bearings checked blades checked electrical connections checked contactors. Unit is working properly at this time.
Springtime HVAC Repair Service for a residential customer near South Dallas. Came out on 1 system service call/maintenance Checked contactors checked capacitors checked pressures checked temp split checked drain lines cleaned condenser coil checked bearings checked blades changed home owner supplied filters checked electrical connections checked Amp draws Found Bad 55/5 run cap Bearing going bad in condenser fan motor Outdoor coil dirty/cleaned Indoor filter dirty/changed Burnt high voltage wire to furnace Dirty return vents on ground /cleaned Unit low on r22 Repairs are recommended at this time though not advised due to conditions overall of unit.
Springtime Plumbing Repair for a residential customer near Exall Park. Upstairs lavatory bowl. Broken drain strainer down stairs bathtub. Shower valve needed temperature adjustment. Replaced drain underneath lavatory bowl. Checked for leaks no longer leaking. Adjusted temperature for down stairs shower valve to 120 degrees. Customer happy
Springtime Plumbing Repair for a residential customer near Deep Ellum. On arrival Brian said water was leaking from under stairs. Ran water from every fixture to replicate the leak. Ran sewer camera to ensure line had no problems. Sewer line was clear other than toilet paper inline. Installed 3 new brass caps.
Spring HVAC Maintenance for a residential customer in Dallas. Checked pressures, cleaned condenser coil, checked filter, checked temp split, checked run capacitors, checked contactor, checked bearings, checked blades, checked electrical connections, and cleared drain line to complete the maintenance service.
Spring Air Conditioning Repair for a residential customer near Ridgewood Park. Installed a Contactor on the air conditioning system, to resolve a/c problems for the customer.
Spring HVAC Maintenance for a residential customer in Dallas. Checked bearings, checked blades, checked drain line, checked filter, checked run capacitors, checked contactor, cleaned condenser coil, checked hard start, checked Amp draws, checked electrical connections, checked disconnect, & checked fuses. Customer pleased on departure.
Spring Residential Air Conditioning Maintenance Service. Came out on 2 system maintenance Checked pressures checked temp splits checked drain lines changed 20x25x1 this visit 20x25x4 is OK still checked bearings checked blades checked contactors checked capacitors checked Amp draws checked electrical connections checked insulation levels checked ductwork Found Low insulation levels Dirty ductwork No surge protection on 3 pieces out of 4 No IAQ Customer happy on departure.
Spring Thermostat Repair Service for a Residential customer. Came out on service call Honeywell t5 thermostat had a lock on it and code is 3340
Air Conditioning Service for a residential customer in Dallas. Came out on a 2 system maintenance & Checked filters, changed downstairs filter, upstairs filter, is unused/new still checked pressures cleared drains checked electrical connections checked run capacitors checked bearings checked blades checked coils checked ductwork checked insulation checked temp split Found No surge protection No IAQ Dirty outdoor coils
Air Conditioning Maintenance for a residential homeowner in Dallas. Came out for a 1 system maintenance on a 20 yr old Unit & Performed a routine maintenance.
Plumbing repair for a commercial client in Dallas with a leaking bar sink. Reconnected trap arm to bar sink extension nut washer was missing not holding the pipe in place. The leak has been repaired for the business.
Performed a two system maintenance checking cooling. Tenant also said that the breaker for downstairs heat keeps tripping. Checked inside unit amp draws, and capacitors, everything working properly at this time. I did noticed that the indoor unit is calling for a 50amp breaker and is has a 30amp. Will need an electrician to replace breaker for both upstairs and downstairs. Also found oil from blower motor on outter casing indicating bearing in the blower motor are going bad. Recommend replacement of blower motor. Checked outdoor units pressures, capacitors, amp draws and electrical components. Found that both coils need to be cleaned, and found pressures about 2-3lbs low for downstairs system. Recommend doing a leak search to see where system is losing refrigerant. Emailed estimate over. Spoke with jerry and he would like to get a leak search on the schedule for downstairs unit.
Performed a service maintenance in Dallas checked bearings, filters, contactors, drain lines, attic insulation, and all electrical connections. Unit is working properly and recommended cleaning outdoor condenser.
Performed a plumbing inspection checking all stops, toilets, lavatories, hot water heater, drain and functionality of fixtures. Found that the hot side stop leaks when you shut off valve. Found that the stop for cold side handle is broken and hot side will not turn water off. Recommended replacing stops with new supply lines. Homeowner wanted to hold off on repairs.
Performed a three system maintenance checking cooling. Checked inside units, amp draws, blower capacitors and changed customer supplied filters on the upstairs and downstairs, also supplied filter for master system. Filter sizes are aprilaire 410, 20x25x4, 20x25x1. Checked drains and ductwork. Then checked outdoor units pressures, amp draws and capacitors. Found that the contactor for the upstairs was pitted and worn out, found that the capacitor for the downstairs unit was reading 16 out of 45, recommended replacing contactor and the capacitor. With approval replaced parts and tested equipment. System are now operating properly at this time.
Performed a one system maintenance checking heating. Checked inside furnace. Checked all electrical, mechanical and safety components, checked filters, amp draws, and cleaned the flame sensor. Checked heat exchanger and burners. System is operating properly at this time.
1/2" Pro press tee, 3" of 1/2 copper pipe, 3/8" compression angle stop.
Install customer supplied grease trap under 3 compartment sink
Came out on service call no heat. Customer states unit will come on run for a min then shut off and not run for hrs. 2005 furnace and evap coil. (New thermostat) Checking sequence of operations inducer came on good amp draws ignitor came on good readings on it gas valve came on flames started to go and then shut off checked blower run cap 10mfd reading 10.17mfd bearings good on blower motor. Blower motor a little dirty at this time dirty 1inch filter found dirty flame sensor not sensing the flame so shutting off the heating. Cleaned flame sensor. Checked system operations. Let unit run for 15-20mins. No more issues at this time. Unit is back up and heating.
Upon arrival found that RTU 6 was locked out on a error code 20. Found that there was an issue with the VFD. VFD had an error code for deceleration to short. Adjusted deceleration time and had ems turn system on and heat came on. Blower came on. System finished call and everything shut down properly. System is now operating properly at this time.
Checked system and found that there was two ductwork connections loose, and filter was clogged up bad, found W2 second stage heat not connected, replaced filter and reattached duct work. Installed nest thermostat. System is heat at this time.