Chrome Heating & Air is pround to provide Dallas, TX with the kind of heating, cooling and plumbing service we would like for our own families.
It costs around $250-$400 to fix and repair a central air conditioning system in Dallas, TX. Although, the price can vary depending on how severe the problem is and if any replacement parts are required. For example, if your evaporator coil is faulty, it can cost up to $1,200 to replace it. Call us today to get your central air conditioning system repaired !
The price to have a plumber clear a drain in Dallas, TX is typically between $200-$300. Some things that can impact the overall price include the complexity of the issue and the contractor’s hourly rate. Having a plumber clear your drain guarantees that your drain gets cleared correctly and quickly. Additionally, if there are any deeper issues, a plumber will be able to spot those and diagnose them for you. If you need your drain cleared , give us a call today .
Your home air conditioner might have a leak due to:
Some air conditioner leaks can be as simple to fix as replacing dirty air filters, whereas other leaks can be more complex, such as repairing a refrigerant leak. If you are experiencing a leak from your home air conditioner, contact Chrome Heating, Air & Plumbing.
Yes, an air conditioner compressor can be repaired. However, depending on the issue, it may be cheaper to replace your air conditioner compressor rather than repairing it. If your compressor is older or it has required many repairs in the past, it is usually more cost effective to have it replaced with a newer and more efficient compressor. Contact us today to have your air conditioner compressor repaired or replaced .
See how we always meet the home services needs of our Dallas, TX customers and why they consider us their plumber and HVAC company in the reviews below!
for Dallas, TX
Our Reviews by City
Vickey - Dallas, TX
Professional, through, friendly, knowledgeable, communicated with me throughout the process of inspecting and installing
George - Dallas, TX
Very timely, thorough with explanations and covers options where applicable.
Finch - Dallas, TX
Good service and good value.
Gigoux - Dallas, TX
Great service. Had my unit up and running in minutes
xxxPhelps - Dallas, TX
Very happy to see Jorge after two days of no air
I'm reviewing Jorge
xxxAnderson - Dallas, TX
This survey is for our 2nd appointment with Jorge.
Great service price too high
xxxAdams - Dallas, TX
Michael - Dallas, TX
They quickly diagnosed the problem and ordered the needed part immediately.
Best Service to date
Mrs price - Dallas, TX
Jorge was polite and professional and they gave me prompt service with a smile.
Honest fair service with quality work
James - Dallas, TX
Always honest fair service
Vivian - Dallas, TX
Although the serviceman was young, he was very impressive with knowledge of his field and with his people skills I felt respected as a person and valued as a customer
Mia - Dallas, TX
Tim - Dallas, TX
Courteous and knowledgable men. Michaela the receptionist worked us in and was much appreciated.
Andrea - Dallas, TX
Great service, very professional and knowledgeable
Completed 1 system fall matience, left estimate for new kitchen faucet and UV light for air purification. Furnace was operating properly through inspection.
Signed up for 2 system chrome club monthly. Changed blower motor capacitor in smaller unit. And install 2 client provided nest thermostats. As well as 2 system tune up special.
Completed one system fall matience. Units amperages, heating elements, safety switches, and blower motor was checked. Unit was working properly at this time. I left an estimate for insulation. Pictures and estimate attached. Also phone number is system is wrong. Correct number starts with 214
Performed heat check on furnace, unit has some noted water damage, but is working properly.
Dispatch and minor wiring repair. Upon arrival Master bedroom unit wasn't heating.it would ignite and within a few moments unit would shut off. Upon diagnostic blower motor was wired wrong by another person/company. After rewiring blower motor furnace is heating properly. Left estimates for new fall special 2 ton single stage furnace and chrome club membership.
Performed heat check on both heating systems. Tested components of heating systems, both units are working properly at this time. I've included recommendations for when technician comes out in spring to do ac checks.
Performed tune ups on 2 systems. All are operating properly
Conpleted one system fall matience on 7 year old coleman furnace. All safety switches and shut off valves are operational at this time.
One system diagnostic. New system install (Two years old) Found outdoor low voltage wire broken. Re wired and used electrical tape on all connection points along with wire nuts to ensure no exposed wires. Left message for landlord voicemail. Unable to get in contact. Still need to collect invoice total.
Dispatched to check units after customer started experiencing electrical surges about 2 weeks ago. I checked voltages/amperages on condensers and furnaces when units were starting up and running. All amperage and voltages were below maximum manufacture standards and are running properly at this time.
Commercial clean VAV coils and change filters
See hvac call attachment
Completed one system fall inspection on Goodman furnace. Unit is operating properly at this time and heating the house well. No problems detected. Also co.pleted plumbing inspection as well. No leaking water anywhere. All fixtures could be upgraded but as far as functionality plumbing is operating just fine.
Unit was running intermediately turning on and off. After diagnostic drain lines were clogged again. I tore apart the drainlines, cleaned the insides of the pvc and cleared the clog. Unit is running at this time.
Called to downstairs not cooling well on Saturday (ambient temp 104) after inspection of units downstairs capacitor was failing on fan side. I replaced the capacitor and unit is cooling at time of departure
Estimate to replace all rooftop units with split systems OR RTU systems.
Completed one system diagnostic. Upon first diagnosis I thought system was just a couple of lbs low on refrigerat. But when filling the system the TXV started not regulating the refrigerant properly. Recommended replacement of the TXV. Customer paid for the 2lbs of refrigerat and signed up for a monthly club membership.
Drain line pipe had crack in it and was leaking all over floor. Replaced 90 degree pipe and water stopped leaking.
System running upon arrival. Charged system with two pounds of 410-a refrigerant. System cooling at this time.
No cool replaced a burn contactor on a Trane system