Local Plumbers, Heating & AC Repair near Dallas
Chrome Heating, Air & Plumbing is proud to provide Dallas, TX with the kind of heating, cooling system and plumber repair services we would like for our own families. Is it time to replace that old HVAC system? Are your HVAC systems providing the energy efficiency you are looking for? Need emergency air conditioning repair service? We also repair and install tankless water heaters!
Our air conditioning company HVAC technicians and plumbers are background checked and Google Guaranteed.
HVAC & Plumbing Service FAQs
The price to have a plumber clear a drain in Dallas, TX is typically between $200-$300. Some things that can impact the overall price include the complexity of the issue and the contractor’s hourly rate. Having a plumber clear your drain guarantees that your drain gets cleared correctly and quickly. Additionally, if there are any deeper issues, a plumber will be able to spot those and diagnose them for you. If you need your drain cleared , give us a call today .
Your home air conditioner might have a leak due to:
Some air conditioner leaks can be as simple to fix as replacing dirty air filters, whereas other leaks can be more complex, such as repairing a refrigerant leak. If you are experiencing a leak from your home air conditioner, contact Chrome Heating, Air & Plumbing.
Yes, an air conditioner compressor can be repaired. However, depending on the issue, it may be cheaper to replace your air conditioner compressor rather than repairing it. If your compressor is older or it has required many repairs in the past, it is usually more cost effective to have it replaced with a newer and more efficient compressor. Contact us today to have your air conditioner compressor repaired or replaced .
It costs around $250-$400 to fix and repair a central air conditioning system in Dallas, TX. Although, the price can vary depending on how severe the problem is and if any replacement parts are required. For example, if your evaporator coil is faulty, it can cost up to $1,200 to replace it. Call us today to get your central air conditioning system repaired !
See how we always meet the home services needs of our Dallas, TX customers and why they consider us their plumber and HVAC company in the reviews below!
for Dallas, TX
Our Reviews by City
Poor customer service
Brent - Dallas, TX
I was cancelled on multiple times last minute, misled on pricing, and then overcharged for my service with the owner of the company lying directly to me. The actual plumber that performed the work was nice and did a good job.
Lasco - Dallas, TX
Jacqueline - Dallas, TX
As always whenever I need service for my unit the techs at Chrome respond in a timely manner. They know their stuff and are very thorough in their assessment of the problem and how best to correct it. They listen to my concerns and explain what I need in terms I can understand. And they stand behind their work.
Awesome work ethic
Lasco - Dallas, TX
B - Dallas, TX
Sharon - Dallas, TX
Vickey - Dallas, TX
Professional, through, friendly, knowledgeable, communicated with me throughout the process of inspecting and installing
George - Dallas, TX
Very timely, thorough with explanations and covers options where applicable.
Finch - Dallas, TX
Good service and good value.
Gigoux - Dallas, TX
Great service. Had my unit up and running in minutes
xxxPhelps - Dallas, TX
Very happy to see Jorge after two days of no air
I'm reviewing Jorge
xxxAnderson - Dallas, TX
This survey is for our 2nd appointment with Jorge.
Great service price too high
xxxAdams - Dallas, TX
Michael - Dallas, TX
They quickly diagnosed the problem and ordered the needed part immediately.
Best Service to date
Mrs price - Dallas, TX
Jorge was polite and professional and they gave me prompt service with a smile.
Honest fair service with quality work
James - Dallas, TX
Always honest fair service
Vivian - Dallas, TX
Although the serviceman was young, he was very impressive with knowledge of his field and with his people skills I felt respected as a person and valued as a customer
Mia - Dallas, TX
Tim - Dallas, TX
Courteous and knowledgable men. Michaela the receptionist worked us in and was much appreciated.
Andrea - Dallas, TX
Great service, very professional and knowledgeable
Performed one system maintenance checking cooling. Checked inside air handlers amp draw, filter, ductwork, drains then checked outdoor units pressures and amp draws. Everything checks out good on system.
Performed a one system maintenance checking cooling. Checked inside units electrical and mechanical components, capacitor, changed out customer supplied air filter. Checked temperature differential. Then checked outdoor units pressures amp draws and capacitors all looked good. Recommended cleaning outdoor coil and adding a air scrubber to the system. Customer wanted to hold off.
Upon arrival homeowner stated that the system would make a thump sound when shutting off. Turned system on and checked outdoor unit. Turned system off at the contactor and disconnect 5 times each and could not get the system to make the noise. Let system run for 10min and then tried to shut it off again but no sound. Had homeowner outside and couldnâ€™t get the system to recreate the issue. Checked capacitors and hard start all looked good. Explained to homeowner that if it happens again let us know and try to record the sound.
Replace kitchen sink hose that runs to sprayer
Installed filters 2-20x25x1 and picked up ladder
Performed maintenance on both systems. Cleaned condensing coils, took temp reading on supply and return air, checked electrical components, checked amps on compressor and fan motors, checked refrigerant charge on both units, cleared drain lines, adjusted refrigerant on downstairs system (removed 3 lbs of 410a. Recommended adding hard start kits on both systems. Units are operating at this time.
Found condensate drain backing up. Drain was vapor locking between ac drain/trap and main drain line/trap. Cleared day drain line and main drain. Recommended adding a drain safety switch to primary pan. Wired in primary pan. Tested function of safety switch. Cut pvc down spout so unit would drain into main drain line. System is running in cooling at this time.
Upon arrival found coil frozen up will need to return once coil de-iceâ€™s.
Need to cut water off to building to replace angle stop
Contactor and 2 capacitors Changed out new contactor switch that had no voltage coming out, and replaced 2 capacitors that were very low on capacitance with a Turbo, changed provided air filters, got outside unit to come on. Superheat/subcooling and psi's slightly off due to house being 90 degrees with no AC. They are slowly balancing out. Sold membership.
Upon arrival performed one system maintenance check in cooling. Checked inside units amp draws temperature differentials, electrical components, mechanical components, checked drain, checked filter, everything looks good checked outside unit checking pressures amp draws and capacitors. Found that the capacitor was reading 37.9 out of 40 which is borderline bad, also contactor outside was pitted and humming. Found outdoor coil dirty. Made recommendations, customer move forward with washing condenser coil and signing up on maintenance. System is cooling properly at this time.
Need to pull #8 thermostat wire from furnace to thermostat. ( 30 feet)
Changed 2 lavatory faucets one in print shop and one in menâ€™s restroom also changed out pop up assembly also
Customer want systems to be serviced. She does have a maintenance plan (membership). Cleared drain lines, cleaned condensing coils, took temp reading on supply and return air, checked static pressure on duct systems, checked electrical components, checked amps on compressors, blowers, and fan motors, checked refrigerant charge on both units, and ran systems through cooling cycle. Bedrooms unit has a weak dual run capacitor (45/5) recommended replacing capacitor. Compressor is pulling high in rush amps. Recommended a hard start kit to shorten start duration and prolong the life of compressor. Static pressure on duct system is within parameters but on the high end. House is negative pressure due to return being a little small. Customer will address ductwork when she replaces equipment. Main unit isn't running in cooling. Found thermostat wire doesn't have enough conductors to run equipment in cooling and stat is wired wrong. Need to pull new wire from furnace to thermostat (#8). Quoted c
Spring maintenance. Outside coils were dirty causing low subcooling. Cleaned and fixed. Only issue spotted
Spring maintenance, superheat 55 subcooling 0, recommended leak search, did not want to pay for it to be done, she will check warranty with Goodman first.
Nobody home, no answer on phone to confirm appt 2 times
Did Spring maintenance for customer. Discovered a faulty hard start capacitor. Replaced capacitor system is running at this time.
Replace Lavatory Faucet
Checked voltages on thermostat, amps on fans and compressor, cleaned coil. Checked refrigerant charge and suspect leak or faulty evaporator coil, customer requested charge system for now and possibly leak check and fix later.
Found 4 leaks at home, 3 in main level shower and 1 in upstairs shower. We repaired 3 in main floor shower and did not have the parts necessary to repair the one upstairs due to shortage of plumbing fittings. We capped that leak so customer could have water throughout the rest of the home. Returned on March 1st and repaired upstairs bathroom. There are no leaks and water is flowing freely, however water is only lukewarm at shower upstairs, we will have a chrome master plumber come out and look into this issue.
19 seer, complete variable speed air handler with 65 stages. Elite series. 10 parts and 10 years labor.
Replace rpz for chiller make up water
Replace 2 1/2" copper piping outside to chiller. Replace 4 butterfly valves, flanges, insulation and aluminum jacket.