Local Plumbers, Heating & AC Repair near Dallas
Chrome Heating & Air is proud to provide Dallas, TX with the kind of heating, cooling and plumbing service we would like for our own families. Is it time to replace that old HVAC system? Are your HVAC systems providing the energy efficiency you are looking for? We also repair and install water heaters!
Our HVAC technicians and Plumbers are background checked and Google Guaranteed.
The price to have a plumber clear a drain in Dallas, TX is typically between $200-$300. Some things that can impact the overall price include the complexity of the issue and the contractor’s hourly rate. Having a plumber clear your drain guarantees that your drain gets cleared correctly and quickly. Additionally, if there are any deeper issues, a plumber will be able to spot those and diagnose them for you. If you need your drain cleared , give us a call today .
Your home air conditioner might have a leak due to:
Some air conditioner leaks can be as simple to fix as replacing dirty air filters, whereas other leaks can be more complex, such as repairing a refrigerant leak. If you are experiencing a leak from your home air conditioner, contact Chrome Heating, Air & Plumbing.
Yes, an air conditioner compressor can be repaired. However, depending on the issue, it may be cheaper to replace your air conditioner compressor rather than repairing it. If your compressor is older or it has required many repairs in the past, it is usually more cost effective to have it replaced with a newer and more efficient compressor. Contact us today to have your air conditioner compressor repaired or replaced .
It costs around $250-$400 to fix and repair a central air conditioning system in Dallas, TX. Although, the price can vary depending on how severe the problem is and if any replacement parts are required. For example, if your evaporator coil is faulty, it can cost up to $1,200 to replace it. Call us today to get your central air conditioning system repaired !
See how we always meet the home services needs of our Dallas, TX customers and why they consider us their plumber and HVAC company in the reviews below!
for Dallas, TX
Our Reviews by City
B - Dallas, TX
Sharon - Dallas, TX
Vickey - Dallas, TX
Professional, through, friendly, knowledgeable, communicated with me throughout the process of inspecting and installing
George - Dallas, TX
Very timely, thorough with explanations and covers options where applicable.
Finch - Dallas, TX
Good service and good value.
Gigoux - Dallas, TX
Great service. Had my unit up and running in minutes
xxxPhelps - Dallas, TX
Very happy to see Jorge after two days of no air
I'm reviewing Jorge
xxxAnderson - Dallas, TX
This survey is for our 2nd appointment with Jorge.
Great service price too high
xxxAdams - Dallas, TX
Michael - Dallas, TX
They quickly diagnosed the problem and ordered the needed part immediately.
Best Service to date
Mrs price - Dallas, TX
Jorge was polite and professional and they gave me prompt service with a smile.
Honest fair service with quality work
James - Dallas, TX
Always honest fair service
Vivian - Dallas, TX
Although the serviceman was young, he was very impressive with knowledge of his field and with his people skills I felt respected as a person and valued as a customer
Mia - Dallas, TX
Tim - Dallas, TX
Courteous and knowledgable men. Michaela the receptionist worked us in and was much appreciated.
Andrea - Dallas, TX
Great service, very professional and knowledgeable
Found and repaired leaks in crawlspace, leaks were caused by freezing of pies, which caused them to burst.
Repaired 3 copper water line burst in main water line above laundry.
Completed one system fall matience. Unit is straight electric heat. Unit is 10 years old and is working at this time, although customer should start considering saving for a new unit. Changing this unit to a heat pump will save on the electric bill substantially. Pictures stretched.
Dispatched to unit not heating again. I was here Friday. On both occasions the furnace hasn't failed for me when I have it a call for heat. Customer stated that she felt cool air coming out of the supply. She did have the fan setting set to on. I explained how the fan setting worked and the fan would run regardless if it was heating or not. Thermostat was also off when I arrived.
Dispatched to unit not heating. Upon arrival thermostats was set to off and fan was on. After I turned on the heat unit fired right up and was heating. Customer stated it was working intermediately, it would ignite for about 20 seconds and then go out. I cleaned flame sensor as a precaution and unit is running fine.
Completed one system diagnostic. Gas valve had failed on furnace and wasn't letting gas in. Customer is going to get fixed with home warranty
Comperable Furnace replacement.
Customer has replaced gas valve and saw that the blower motor wasn't running immediately. I ran through system and explained that there was a delay on the blower motor. Unit is operating properly upon departure.
Completed estimate on heating garage. The only practical solution that wouldn't cause air flow issues in the house and the space to be heated properly is a mini split system estimate attached.
Performed heat check on heat pump/air handler. Also changed 20x25x4 filter. Unit is in very good shape and working properly.
Performed heat check, also looked at insulation in attic and gave estimate. Will talk with Aaron about giving discount on insulation.
Completed 2 system fall matience. Both units are 21 years of age. Both units blower motor, inducer draft motor and boards are showing signs of failure. Also ducts aren't sealed with mastic at all. I advised customers to be ready to replace system when a major repair arrives.
Conpleted 2 system fall matience on over head units. Checked amperages of heat strips, capacitors, and blower amperages. Both units are working properly at this time.
Completed 1 system fall matience, left estimate for new kitchen faucet and UV light for air purification. Furnace was operating properly through inspection.
Signed up for 2 system chrome club monthly. Changed blower motor capacitor in smaller unit. And install 2 client provided nest thermostats. As well as 2 system tune up special.
Completed one system fall matience. Units amperages, heating elements, safety switches, and blower motor was checked. Unit was working properly at this time. I left an estimate for insulation. Pictures and estimate attached. Also phone number is system is wrong. Correct number starts with 214
Performed heat check on furnace, unit has some noted water damage, but is working properly.
Dispatch and minor wiring repair. Upon arrival Master bedroom unit wasn't heating.it would ignite and within a few moments unit would shut off. Upon diagnostic blower motor was wired wrong by another person/company. After rewiring blower motor furnace is heating properly. Left estimates for new fall special 2 ton single stage furnace and chrome club membership.
Performed heat check on both heating systems. Tested components of heating systems, both units are working properly at this time. I've included recommendations for when technician comes out in spring to do ac checks.
Performed tune ups on 2 systems. All are operating properly
Conpleted one system fall matience on 7 year old coleman furnace. All safety switches and shut off valves are operational at this time.
One system diagnostic. New system install (Two years old) Found outdoor low voltage wire broken. Re wired and used electrical tape on all connection points along with wire nuts to ensure no exposed wires. Left message for landlord voicemail. Unable to get in contact. Still need to collect invoice total.
Dispatched to check units after customer started experiencing electrical surges about 2 weeks ago. I checked voltages/amperages on condensers and furnaces when units were starting up and running. All amperage and voltages were below maximum manufacture standards and are running properly at this time.
Commercial clean VAV coils and change filters
See hvac call attachment